With the general production and application of cooling towers, the editor of Teling below will introduce some practical factors for the usual leakage of closed cooling towers. You can actually see the following.
Water leakage is one of the common problems of closed cooling towers. However, according to our conventional methods, most of the closed cooling towers are made of stainless steel plates or galvanized steel plates, and the cooling water is also circulated in closed copper pipes, and there should be no leakage. .
In the process of assembling the closed cooling tower, the aluminum-zinc plates are all rubbed with glue to carry out compaction and sealing. Long-term operation, the impact of spray water, the deformation of the basin, and the drop of sealant all cause water leakage at the joint. Because the spray water is concentrated in the pool at the bottom, leaking water means that the spray water needs to be continuously filled. The closed cooling tower section is all aluminum-zinc plated, which can be filled with sealant from the inner gap of the closed cooling tower to prevent leakage.
This is mainly because of the long-term application, and it is also possible that the environment and water quality of the local application have high acidity and alkalinity. The material of the collection and storage tank has been corroded. The thickness of the tank shell is uneven, which is convenient in the thin and relatively thin places. A damaging water leak will occur. Water leakage will increase water consumption, increase environmental pollution, and accelerate the corrosion of other accessories and poor circulation. If it is a glass fiber reinforced plastic closed cooling tower, we can choose to clean the surface layer, polish and clean it, use a cleaning agent to degrease, use epoxy repair agent and glass fiber tape to carry out the reinforcement method, if it is the material of aluminum-zinc plate, consider To the replacement part of the galvanized sheet.
This is very rare. You have to contact the pump manufacturer in time, saying that the pump leaks will cause the pressure to be unstable and affect the circulating water system.
In the process of pipe layout, some flanges and elbows will be connected. During the process of connection, a sealing ring will be added between the two joints. The pipeline leaks. Most of the factors are that the pipeline is not tightly connected. , The sealing ring is damaged or the position displacement is caused by the weak sealing, resulting in water leakage.
For more information about closed cooling towers, please follow our official website at any time. Welcome new and old customers to inquire.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen