Closed cooling tower packing, as the medium for the exchange of heat and humidity between gas and cooling tower, is generally made of high-grade PVC material, which is a type of plastic product, and is very simple to clean. When you see dust or microorganisms adhering to it, you can clean it under pressure with water or detergent. It is easy to see when there is dirt or microorganisms in the drip tray, and it is very simple to clean it by washing it. But it should be noted that before cleaning, plug the drain of the cooling tower and open the drain valve during cleaning to allow the cleaned dirty water to drain from the drain to prevent it from entering the cooling water return pipe. When cleaning the water distribution equipment and fillers, it is necessary to operate the control in this way. For those that use transmission belts to reduce the speed of machinery and equipment, check the tightness of the rotating transmission belt once every half a month, and adjust it if it does not comply with the order. If the elasticity of several transmission belts is different, they must be replaced as many as possible: If the closed cooling tower manufacturer does not operate for a long time, we can remove the transmission belt for storage.
1. The surface of the foundation machinery and equipment is cut flat and guaranteed to be on the same water surface, and the center line of the lower column and the lower water inlet is vertical to the bottom edge. Ensure that the lower column and the lower water inlet are in excellent contact with the foundation, and the foundation is embedded with steel plate.
2, pay attention to ensure that the diameter error of the upper tower body vent should be as small as possible after the tower body is divided and assembled.
3. When using a circulating water pump, pay attention that its flow is consistent with the cooling water volume (referring to: combination). When using it, keep the cooling tower within ±5% of the design volume to prevent excessive and harm the cooling efficiency.
4. Make sure that the arc-shaped surface of the gasket fits the arc-shaped surface of the tower rib root, and the assembly and assembly of the lower shell should be watertight.
5. The fan should be exhausted upward from the machinery and equipment. The gap between the blade end of the fan and the tower body should be symmetrical and not more than 100mm. The four blades should be adjusted at the same angle, and the plane of the impeller rotation should be vertical to the center line. The closed cooling tower is a comprehensive material integrating various disciplines such as aerodynamics, thermodynamics, fluidics, chemistry, biochemistry, materials, static and dynamic structural mechanics, and production technology.
6. It is stipulated that the surface of the machine and equipment of the water-sprinkling filler layer is flat and the spacing is even. The closed cooling tower is a comprehensive material integrating various disciplines such as aerodynamics, thermodynamics, fluidics, chemistry, biochemistry, materials, static and dynamic structural mechanics, and production technology.
7. The power supply must have a safety method. After the power cord is connected, the motor junction box should be sealed to prevent water (to avoid mold and deterioration) air entering and burning the motor.
8. The orientation of the water inlet and outlet pipes of the closed cooling tower can be adjusted according to the specific conditions of the construction site and the direction of changing the screw holes on the flange.
The above is about the precautions for cleaning and maintenance of closed cooling towers. I hope that you can learn more about closed cooling towers. If you want to know more about the selection of closed cooling towers, welcome everyone Go to trlon air conditioner official website to learn more.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen