The consumable parts in cooling tower accessories: cooling tower motor bearings, reducer bearings, reducer transmission belts and other small parts are consumable parts. Generally, the ageing condition will occur in the time period around 1 year, and it must be immediately Dismantle and replace to prevent abnormal noise of cooling tower fan vibration.
Regular maintenance or replacement parts in cooling tower accessories:
(1) The normal use of cooling tower packing before and after 3 years is usually due to the weathering layer or too much fouling. The cooling tower packing must be cleaned or the cooling tower packing must be removed. If the water quality is turbid or the pH is strong, the cleaning should be carried out before and after 2 years. .
(2) The weathered layer phenomenon will also occur in the cooling tower water collector before and after 3 years of use. At this time, corresponding maintenance or disassembly must be carried out to prevent fouling and blockage, which will harm the actual effect of temperature reduction.
(3) The cooling tower fan is the key part of the cooling tower, and it is also the most important part of the cooling tower maintenance. The maintenance personnel of the site must add butter on time and check the waterproof condition of the motor. If the noise standard of the cooling tower rises significantly, the power of the cooling tower fan must be balanced at this time. If the cooling tower fan is destroyed by natural disasters or man-made damage to the wind blades or damaged, it must be shut down and repaired immediately, and replaced New fan (it is not recommended to dismantle and replace the damaged fan blades separately, it is impossible to keep the fan direction balanced).
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen