The cooling tower dehydrator is a very important part of the cooling tower. Today, the cooling tower manufacturer China Trlon Air Conditioner introduced the functional principle of the cooling tower water remover.
Cooling tower dehydrator is a device used to collect flowing water in a closed cooling tower. It is usually located at the upper part of the cooling tower, below the induced draft fan. The quick installation of the fan drives the air flow in the cooling tower, and the moisture in the air is driven by the fan to sit down and flow upwards. After evaporation, the cooling tower is mixed with air. When passing through the cooling tower water eliminator, water adheres to the cooling tower water eliminator and gradually accumulates. When the gravity of the formed water droplet is greater than the adhesion force, it will fall into the pool or prepare to attach to the condenser coil to evaporate again.
The cooling tower dehydrator is a water blocking absorption device placed above the filler of the open countercurrent cooling tower or on the side of the spray system of the closed cooling tower. Its function is to let the hot air flow pass through in a corrugated manner, block and absorb the water droplets in the hot air flow, so as to achieve the purpose of removing water or absorbing water. Therefore, the cooling tower water remover is also called the cooling tower water absorber.
The cooling tower water remover can effectively reduce the flow rate of the cooling tower water and save water. Cooling tower eliminators are usually assembled from plastic materials. The blades of the cooling tower water remover are supported by nails and screws at both ends, and are stacked by multiple layers of plastic or glass fiber reinforced plastic. The water collector of the cooling tower has a very high water collection efficiency and will not reduce the air flow in the cooling tower. When the hot and humid air in the tower passes through the dewatering device of the cooling tower, it can block 75%-90% of the water, reducing the grace rate to less than 0.001%. The main components of the cooling tower water remover are: pvc plastic water catching piece, bracket, tie rod, plastic nut, splash-proof device and so on.
The use of the cooling tower water remover has passed the effective test of large condenser equipment in the metallurgical industry and foundry industry, and has achieved good water-saving effects. Compared with the open cooling tower, the closed cooling tower effectively improves the water saving efficiency to a certain extent due to the fully enclosed design. The design of the cooling tower water remover further improves the water saving effect of the closed cooling tower.
The cooling tower water eliminator plate is extruded from glass fiber reinforced plastic material or polyvinyl chloride material, and imported carbon black is added as an additive to the cooling tower water eliminator plate, which greatly improves the anti-ultraviolet and anti-aging performance of the plate. Cooling tower dehydrator has the advantages of high water collection efficiency, low air flow resistance, high strength, no deformation, convenient installation and maintenance, long service life, and good flame retardancy.
The above is the introduction to the function of the cooling tower dewatering device. I hope everyone can understand this accessory of the cooling tower. For more cooling tower problems, you can continue to pay attention to the trlon air conditioner website.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen