China trlon is a company engaged in the maintenance of cooling towers, mainly engaged in various round counterflow cooling towers, square counterflow low-noise cooling towers, square cross-flow low-noise cooling towers, industrial water towers, cooling tower accessories, cooling tower motors, reducers, fabrics Water heaters, sprinklers, sprinklers, cooling tower fillers. Contracting Jiangsu and Zhejiang cooling tower maintenance and other large central air-conditioning cooling tower repairs around Shanghai, industrial cooling tower repair and maintenance services, cooling tower filler replacement, water distributor replacement, collection basin Plugging repair, steel structure reinforcement, wind motor balance adjustment, reducer maintenance and replacement bearings and cooling tower dismantling and migrating machine.
Maintenance cooperation brands have opportunities for cooling tower repairs, Marley cooling tower repairs, Jinri cooling tower repairs, air research cooling tower repairs, and Speedy cooling tower repairs. The company adheres to the business philosophy of "customer first, forge ahead" and adheres to the principle of "customer first" to provide our customers with high-quality services. Welcome to inquire.
In the long-term operation of the cooling tower, the following problems will generally occur:
1. Fan problem. If the air volume is insufficient, the angle of the fan blades and the belt can be adjusted appropriately. But if the fan blade is broken, there is no other way but to replace it. And one blade is broken, and all the blades need to be replaced. Of course, there are many problems with fans, such as the blades and the air ducts, and the vibration of the blades. This requires on-site testing and analysis.
2. Motor problem. The motor problem is simple, nothing more than heat, burnout, vibration, etc. This is related to the quality of the motor, and vibration may be related to bearing wear. Specific analysis of specific problems, most of which can be solved by repair or replacement.
3. The water collector is damaged. Generally, cooling towers that have been used for many years will have the problem of damage to the skimmer. The breakage of the skimmer will cause water mist to splash and the rate of water floating will soar. It is a waste of water, and it is easy for Legionella to be inhaled into the respiratory tract, causing disease outbreaks. When Wuxi Greenland Cooling Equipment Co., Ltd. deals with the problem of the water collector, it generally tries to repair the original water collector as much as possible, and replace it with a new one if it is damaged and needs to be replaced.
4. The water pipe problem. The cooling tower pipes are prone to bending deformation, blockage, corrosion and perforation. Generally, such problems cannot be repaired, only replacement of new accessories. Shanghai Lanrui has a variety of standard cooling tower accessories, and can also be made non-standard according to the user's old cloth water pipes.
5. The nozzle problem. The nozzle is generally broken, clogged and other problems. The price of replacement nozzles in our company is low, so we generally use all replacements.
6. Filling problem. The packing problem is nothing more than aging or fouling. The aged packing must be replaced, and the packing with excessive fouling or silt can be considered for cleaning. At the cooling tower site, trlon will always give you the best solution.
7. Closed cooling tower coil problem. Closed cooling tower coils may perforate after a certain number of years of use, or they may become fouled on the outside. Severely fouled coils will not be able to dissipate heat. For the leaked coil, it is almost impossible to repair, only to be replaced. For coils with serious surface fouling, cleaning or proper maintenance can be considered, and coils with particularly serious fouling can only be replaced.
8. There are several reasons why the water distribution rotor does not rotate: the water distribution pipe is crooked, the water pressure is insufficient, and the water distribution rotor is broken. Prescribe the right medicine for different problems.
9. The inlet louver is damaged. Broken air inlet louvers can cause water splashing in the cooling tower. It can be replaced according to different intake louvers.
We provide Shanghai cooling tower repair and maintenance, Jiangsu cooling tower cleaning service, and develop corresponding maintenance plans according to the different conditions of the customer's cooling tower
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen