With the continuous use of closed cooling towers, the cooling effect is also reduced to varying degrees. To ensure the normal operation of the closed cooling tower, the cooling tower must be regularly inspected and maintained on time. There are many reasons that affect the cooling effect of the cooling tower. Let's follow the cooling tower manufacturer trlon to understand the reasons that affect the heat dissipation of the closed cooling tower!
1. Operating environment. Closed cooling towers need to be arranged in air circulation areas, so we have already seen many cooling towers arranged on the roof or above the production workshop. After arranging the cooling tower, minimize constructive work near the cooling tower and affect the air circulation environment of the cooling tower.
2. Fan and air volume. If the cooling effect is reduced, check whether the air volume of the fan and cooling tower is sufficient. The air volume is affected by the fan. Let us routinely check whether the fan's leaf angle is displaced and whether the leaf is damaged. There is a certain gap between the nylon fan blades and the stainless steel fan blades in use. Modify the fan angle to improve the shaft lubrication.
3. Spray water. During the operation of the closed cooling tower, we can hear the rumbling noise inside. If there is less water, the calorie loss will be reduced. Water reduction and the pump have an impact. Routinely check whether the working pressure of the pump is stable and there is no air in the pump. Routinely check whether the pipeline is blocked.
4. The spray system is the key component of the condensing copper pipe, and the nozzle is the component to be tested. The water spray is evenly symmetrical, it can cover the entire solidified water circle and prevent dry spots and cause fouling.
5. The question of scale. The formation of scale has a certain impact on the sprinkler system. The main reason is that the uneven distribution of water in the hydration equipment leads to the formation of dry spots on a little cooling copper pipe. After the water volatilizes, the cracking point will solidify calcium and magnesium ions. , The scale will form for a long time. The formation of scale will accumulate and affect the heat dissipation effect.
The good use of closed cooling tower can extend the service life and ensure the cooling effect of the cooling tower. Our manufacturer recommends that we maintain and replace the water on time when using a closed cooling tower. If the water quality is not good, scale will form quickly and there will be more ditches, so it must be cleaned frequently, which will result in higher operating costs.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen