With the popularization of production and use of cooling towers, the editor of trlon air conditioners below will analyze the specific reasons for the daily water leakage of closed cooling towers. For details, please see this article.
Water leakage is one of the common failures of closed cooling towers. However, according to our normal thinking, most of the closed cooling towers are made of stainless steel or galvanized steel. The cooling water also circulates in the closed coil, so there should be no leakage.
When assembling the closed cooling tower, glue is applied between the galvanized steel sheets for compaction and sealing. Long-term operation, the impact of spray water, the deformation of the basin, and the fall of the sealant will cause water leakage at the connection. Because the spray water is concentrated in the bottom of the pool, the leaking water needs to be continuously supplemented with spray water. The closed cooling tower sections are all aluminum-zinc plates, which can be filled with sealant from the inner gap of the closed cooling tower to stop leakage.
This is mainly due to long-term use, and it may also be caused by the environment and water quality caused by the high pH of the water used in the local area. The material of the water collection tank has been corroded. The thickness of the tank is uneven, and damage will appear in the thinner part. Sexual leakage. Water leakage will increase water consumption, aggravate environmental pollution, and then accelerate the corrosion of other components, a vicious circle. If it is a glass fiber reinforced plastic closed cooling tower, we can clean the surface, polish it, degrease with a cleaning agent, and use epoxy repair agent and glass fiber tape for reinforcement. If it is made of aluminum-zinc plate, consider replacing the part. Of galvalume.
This is very rare. You have to contact the pump manufacturer at time, saying that the pump leaks will cause pressure instability and affect the water circulation.
When arranging pipes, some flanges and elbows will be connected. When connecting, a sealing ring will be added between the two joints. The pipeline leaks. Most of the reasons are that the pipeline is not tightly connected and the sealing ring Damage or position displacement will cause the seal to be weak and cause water leakage.
For more inquiries related to closed cooling towers, please follow our official website at any time, and welcome new and old customers to inquire.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen