Get the latest information and prices of cooling towers? We will reply as soon as possible within 24 hours
( Items with * are required)
Before operation, the cooling tower should check whether the matching of motor and fan meets the design requirements. When the cooling tower starts, the water pump should be turned on first and then the motor should be turned on. The motor is not allowed to run without water dousing. Adjust the Angle of the cooling tower nozzle according to the water supply.
What points should be paid attention to in the use and maintenance of the compound flow closed cooling tower after the installation is completed? Next, the professional technicians of Trlon Energy Saving Air Conditioning Equipment Co., Ltd. will introduce to you!
1, the cooling tower before operation should check whether the motor and fan matching meet the design requirements.
2. Before operation, check whether the fan is vertical to the foundation, the clearance of the fan blade body should be uniform, whether it is flexible to rotate by hand, and there is no stagnation phenomenon, otherwise it can not be energized.
3, the motor should be refueled before operation, such as reducer should use hyperbolic gear oil or HL30# gear oil, can not use ordinary oil, refueling from the refueling pipe input, oil level is added to the middle of the oil needle scale Z line after the oil needle cover tightly.
4. When the cooling tower starts, the water pump should be turned on first and then the motor should be turned on. The motor is not allowed to operate without water pouring.
5. Adjust the Angle of the nozzle of the cooling tower according to the water supply.
6, After the cooling tower is powered on, the motor and fan should run in balance, without abnormal sound. The motor current should not exceed the rated value, otherwise it should be stopped for inspection.
7. After continuous operation for 1 hour, stop the machine to check whether the fasteners are loose and whether the sealing parts leak oil. After the inspection meets the requirements, the machine can be officially started.
1. Before the cooling tower is put into operation, the flow channel of circulating water pumps such as pipes, water pumps, heat exchangers, equipment and collecting tanks should be thoroughly cleaned. Flushing water should not enter the cooling tower to prevent blocking the pouring filler and equipment.
2. The newly installed motor and fan should be stopped for inspection after 15 days of operation. If there is a reducer, please check it every six months to a year.
3. Check the packing and water filling pipe regularly, and clean up in time if scale appears. If the water contains acid, alkali and other liquids, please check the internal FRP anti-corrosion steel components once every three months. If corrosion occurs, please contact us for anti-corrosion treatment in time.
4, the establishment of cooling tower overhaul, minor repair system. Overhaul once every three years, minor repair is the corresponding cleaning and replacement of the packing and water distribution nozzle, the maintenance and maintenance of the fan and motor before the arrival of the summer every year.
5. Carry out anti-corrosion treatment on the steel structure parts every year, and clean the cooling tower pool.
The above is all the content of the compound flow closed cooling tower introduced by the professional and technical staff of Trlon Energy Saving Air Conditioning Equipment Co., Ltd. I hope to help you. If you want to get more information, please pay attention to our website!
( Items with * are required)
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen