Today, the cooling tower repair manufacturer China trlon air conditioner introduced us to the protection and maintenance content of the cooling tower.
The cooling tower is corrosion resistant, high compressive strength, light weight, small size, less floor space, low engineering cost, beautiful and durable, and easy to transport, install and repair. Therefore, it is widely used in various social units, and is particularly suitable for cooling circulating water circulation such as central air conditioning, refrigeration, air compressor stations, heat treatment furnaces and cooling processing techniques. Now let's share with you what the protection and maintenance content it needs.
The cooling tower equipment should be shut down, and the pipes should be carefully cleaned up. The water collector, the surface of the filling material and the collection tank and other items and dust should be carefully cleaned to prevent clogging. Before the cooling tower is used, it is necessary to start a trial operation. Check whether the centrifugal fan. The tower is stable, whether everything is normal when the rotating nozzle is running, whether the nozzle is evenly distributed, and whether the motor is waterproof and so on.
When the cooling tower is used, you should always check the operating conditions of the centrifugal fan, including the amount of current, operating voltage, centrifugal fan vibration, noise, oil level, whether there is oil leakage or whether the timing belt transmission is loose, and whether there is deviation. Is everything normal and so on.
Gearbox uses 20# mechanical lubricating oil or engine oil. In addition to the usual continuous addition to the specified oil volume, it should be replaced as many times as possible every year during successive operations.
The timing belt transmission belt seat bearing should be filled with grease. Usually, it is filled with a grease gun once a month, and it is disassembled and replaced once every year after continuous operation. Always pay attention to the firmness of each butt joint member. Anchor bolts.
The turbidity of the cooling tower's seepage water should not exceed 10mg/liter. During operation, it should be based on the water body conditions, taking into account punctual sewage treatment or adding water body stability treatment.
The original material of the filling material adopts modified material, high temperature resistant hard polyethylene (PVC), or heat resistant polypropylene (PP).
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen