In summer, with the increase of outdoor temperature and wet bulb temperature, the main reasons for the unsatisfactory cooling effect of the cooling tower are as follows:
1. The cooling tower model selection is too small or the cooling tower manufacturers cut corners and materials, and fail to produce according to the standard configuration; with the increase of cooling tower manufacturers and the economic decline in recent years, in order to maximize profits, cooling tower manufacturers do not hesitate to cut corners and shoddy materials. Reduce costs; here, Lingdian cooling tower reminds users and friends that the cooling tower must be selected according to the temperature and flow of the incoming and outgoing water. The cooling tower with the same price and the same configuration must be large in size; don’t try to choose the standard cheaply. There are cooling towers with tons of cold, because you still suffer losses.
2. Uneven water distribution; if the sprinkler is damaged or the water distributor does not rotate, the water distribution should be even if it is distributed by the sprinkler system or the rotating water distributor.
3. The air volume of the cooling tower fan is too small; the angle of the fan blades can be adjusted appropriately.
4. The installation location of the cooling tower is improper; the cooling tower should be installed in a cool, airtight place, and not in a closed environment around it.
5. The cooling tower packing is blocked; once the cooling tower packing is blocked, the circulating water will flow eccentrically. Each piece of cooling tower filler has a texture. Once the texture is blocked, it will cause uneven film formation on the surface of the cooling tower filler, which directly affects the cooling effect.
6, the flow or pressure of the water pump is too large;
7. The outdoor temperature is too high and the wet bulb temperature is too high; in this case, water can only be properly replenished to reduce the water intake of the cooling tower or increase the alarm temperature required by the equipment.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen