The high-temperature glass fiber reinforced plastic cooling tower is a heat dissipation device. It is a kind of steam that uses water and air flow to exchange cold and heat after touching. The waste heat generated in the refrigeration and air-conditioning is used to reduce the water temperature by the transpiration heat sink to ensure the normal operation of the system.
Product performance and selection of high temperature glass fiber reinforced plastic cooling tower:
1. Planning parameters: Industrial towers are: air wet bulb temperature τ=28℃, inlet water temperature τ1=42℃, outlet water temperature τ2=32℃
2. When selecting a tower, it is necessary to know the cooling water quantity Q, the inlet water temperature t1, the outlet water temperature t2, and the air wet bulb temperature τ, and then determine the model according to the thermal performance curve.
3. The material of the industrial FRP cooling tower can withstand the low temperature of -50℃, but the area where the average temperature of the cold month is lower than -10℃ should be clarified in order to adopt the anti-icing method.
4. The turbidity of the circulating water is not more than 50 mg/L, and it is not more than 100 mg/L in the short term. It should not contain oil and mechanical impurities. When necessary, measures to eliminate algae and stabilize water quality shall be adopted.
5. Refer to the "Foundation Buried Plate and Load Table" for the load on the foundation of the high temperature glass fiber reinforced plastic cooling tower.
6. The direction of the water inlet and outlet pipes of the round high temperature glass fiber reinforced plastic cooling tower can be rotated at 90°, 180°, and 270°.
7. The water distribution system is planned according to the nominal water flow. If the difference between the actual water volume and the nominal water volume is more than ±15%, it should be clarified when ordering to modify some data.
8. The inlet water temperature of the cooling tower does not exceed 60℃. If it exceeds 60℃, it should be stated when ordering.
9. The viewpoint of the fan blade device is adjustable, but the viewpoint must be the same. And the current of the motor does not exceed the rated current of the motor. Refer to the circular countercurrent tower for the adjustment method.
10. The fan can be reversed at low speed for a short time to eliminate ice.
FRP cooling tower cooling water tower application scale:
is mainly used in air conditioning cooling systems, refrigeration series, injection molding, tanning, foaming, power generation, steam turbines, aluminum profile processing, air compressors, industrial water cooling and other fields. Most applications are air conditioning cooling, refrigeration, and plastic chemical industries.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen