Cooling water tower anti-corrosion, steel structure anti-corrosion, sewage pool glass fiber reinforced plastic anti-corrosion, furnace frame anti-corrosion, pipeline anti-corrosion insulation, wind turbine tower anti-corrosion (cleaning, spraying, maintenance), various iron tower anti-corrosion, cooling tower anti-corrosion (platform , Straight climbing ladder, protective net), anti-corrosion of storage tank. New cooling tower platforms, signal lights assembly and replacement, cooling tower assembly straight ladders and other high-altitude operations projects have a pass rate of %. In recent years, trlon has excellently completed many project repairs and renovations.
Waterproof plugging construction steps for cooling tower chassis:
1. Preparations before the cooling tower waterproof plugging and bonding:
①The bonding place must be dust-free and not wet and cold;
②The blending of epoxy resin and hardener: 1Kg is suitable for each time, and it cannot be higher than 2Kg. After using it, adjust and use again. The percentage is 1Kg epoxy resin. Use 10cc hardener.
2, Cooling tower waterproof plugging and bonding method:
First use a brush to coat the blended epoxy resin, then paste the glass fiber, and then coat the epoxy resin, repeat two to three times.
3. Common precautions for waterproofing and plugging cooling towers:
①It takes 6 hours for the adhesive to be applied, and no pressure or trampling is allowed;
②The glass fiber should not be wet or cold before application. If it is wet or cold, it must be dried before it can be used.
The above is the reason for the leakage of the cooling tower chassis and the repair method. I hope to help everyone. Therefore, everyone needs to fully consider this before construction to avoid many unnecessary problems in the middle and late stages.
Square cooling tower anti-corrosion
Cooling tower anti-corrosion construction steps:
A. Fix the leaves of the exhaust fan with hemp rope at the upper end of the cooling tower to prevent the leaves from rotating and causing injuries to employees.
B. Take a ladder to enter the cooling tower from the exhaust fan at the upper end of the cooling tower, disassemble the old packing inside one by one, and place it according to the point selected by Party A.
C. Clean the inner and outer walls of the cooling tower, and the surface of the supporting steel frame inside shall be treated with rust prevention, and Party A shall be notified whether the corroded steel frame needs to be replaced according to the corrosion status, and the assembly screws are firm.
D. Check each sprinkler device, and replace it according to the situation. Note: The spray device is brought by Party A.
E. Water basin and cooling tower shell are used for leak-proof maintenance.
F. Brush the anti-rust paint on the steel frame more than 2 times.
G. After the paint is dry, assemble the new filler in the cooling tower.
China trlon air conditioner focuses on the product research and development, design, production, sales, assembly, cooling tower maintenance and refrigeration engineering of central air conditioning cooling equipment. Cooling tower maintenance and transformation related services include: contracting major brands of cooling tower filler replacement, cooling tower dismantling and replacement, cooling tower parts replacement, cooling tower sound insulation and noise reduction, cooling tower anti-corrosion and waterproof plugging, cooling tower maintenance, circulating water Cooling system engineering, etc. The service scope covers Dongguan, Shenzhen, Guangzhou, Huizhou, Foshan, Zhuhai, Zhongshan, Shantou and other places, and is committed to building a high-quality cooling system and supporting facilities service project manufacturer.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen