FRP cooling towers are a kind of common refrigeration equipment when in use. In practice, in order to effectively ensure that the equipment is used for a longer period of time, in addition to basic inspection and cleaning work for the equipment, it also needs to be done regularly Maintenance work.
FRP cooling towers are generally equipped with water-cooled chillers for use. For cooling towers that use belt deceleration devices, the belt should be shut down every two weeks to check the tightness of the belt, and adjustments should be made if it is not suitable. If the cooling tower uses a gear reduction device, then stop the machine every month to check the oil level in the gearbox, and if the oil is insufficient, it must be refilled.
The color and viscosity of the oil must be checked every six months of operation of the glass fiber reinforced plastic cooling tower, and all the oil must be replaced if it fails to meet the requirements. The motor of the cooling tower fan works in a hot and humid environment for a long time. In order to ensure its insulation performance and prevent the motor from burning down, the motor insulation test must be done once a year.
FRP cooling towers should pay attention to check whether the packing is damaged, and if there is any damage, it should be repaired or replaced in time. The grease of all bearings in the fan system is generally replaced once a year. When using chemical agents for water treatment, pay attention to the corrosion of the fan blades; in order to slow down the corrosion, remove the corrosive substances on the blades once a year and apply the anti-rust paint evenly. Or paint a layer of 0.2mm thick epoxy resin on the blade.
The preparation before use of FRP cooling tower and the maintenance during operation, in order to enable FRP cooling tower to perform the best function, thereby extending the life of FRP cooling tower, then good inspection and maintenance must be done. Under normal circumstances, it is necessary to conduct a comprehensive observation of the FRP cooling tower every day to ensure its normal operation.
FRP cooling towers need to be thoroughly inspected and cleaned when working. And the work part needs to do a more detailed inspection, and wait until there are no problems before it can be carried out. After passing the inspection door and entering the tower, it is necessary to clean up the debris and silt on the bottom basin of the cooling tower, and to check whether the pipes are blocked. Use high-pressure water to wash the heat sink film and the soil on the bottom basin of the cooling tower, and drain the sewage through the drain.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen