The closed cooling tower is a shell-and-tube heat exchanger placed in the tower, with the help of the heat exchange of circulating gas, spray water and circulating water to ensure the cooling effect. The following is a brief introduction to the maintenance of the closed cooling tower of the Kangming closed cooling tower for you.
Due to the use of T2 copper tubes and stainless steel heat exchangers, the closed cooling tower adopts aluminum alloy cooling fans and evaporative condensers for dual heat dissipation, and closed cooling liquid circulation. It is widely used in petroleum, chemical, foundry, thermoelectric and other industries. .
There is a big difference between using a cooling tower in winter and using it in summer. In summer, the environment temperature is high, so the heat exchange will be affected, and the temperature of the spray still cannot drop. The cooling tower temperature is high in summer, and the solution is difficult to cool down.
Precautions for cooling towers during operation and rest in winter: 1) Drain circulating water and spreading water. 2) In the case of a closed type, please open the circulating water drain, exhaust port, and drain valve of the diffuser water pump.
Some introductions of cooling tower manufacturers for cooling tower maintenance, setting up the site, and cooling heat-resistant temperature
What is the calculation method for the water supply of the air conditioning cooling tower? Water loss by evaporation (E) E = Q/600 = (T1-T2)×L/600; E represents the amount of evaporated water (kg/h); Q represents the heat load (Kcal/h); 600 represents the latent heat of evaporation of water (Kcal /h); T1 represents the water temperature (℃)
How many water pumps does a closed cooling tower need? There is no immediate response to this question, because in the case of the overall design of the fluid cooling tower, in the refrigeration plan presented by the customer, it is generally carried out with water pumps based on specific conditions.
With the popularization of production and use of cooling towers, the editor of trlon air conditioners below will give you an analysis of the specific reasons for the daily leakage of closed cooling towers. For details, please see the analysis in this article.
Everyone should not be unfamiliar with closed cooling towers. Then everyone knows what impacts the daily closed cooling towers will cause when the drainage is not clean. Below trlon air conditioners will take you to analyze the serious consequences and the serious consequences of unclean drainage of closed cooling towers. Performance characteristics
Cooling towers usually have specific noises such as fan noise, tower vibration noise and water splashing noise. Next, I will introduce to many friends the importance of cooling tower noise treatment and the corresponding noise reduction treatment solutions! The importance of cooling tower noise treatment is expressed in the following points:
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen