In the cooling tower operation process must ensure the normal operation of the reducer, which requires the staff to regularly maintenance of the reducer. Turing cooling tower manufacturers for everyone to share the maintenance of cooling tower reducer.
1, the new device of the reducer, after a week of operation, the machine should be put clean oil, in order to run in the process of iron out of the machine, and add clean oil from the beginning.
2, the new device or after overhaul of the reducer, in the new operation of the month, should stop once a week to check the oil level, and measure the load (current) overload, make the operation record. During this period, if the main shaft of the reducer is found to leak oil, it should inform the factory to deal with it in time. If the oil level trace drop, it is a normal scene, should be timely replenishment of the transpiration lubricating oil.
3. If the reducer operates continuously for half a year, the lubricating oil should be replaced once to avoid the lubrication effect after the lubricating oil is oxidized.
4. The oil seal of the reducer and the seal on the shaft of the inverted-type reducer are all attributed to vulnerable parts, and they should be replaced every 12 months to ensure the reliability of the seal.
5, because the reducer is started under full load, the impact force is very big, the gear is simply damaged, and the start time is long, which is bad for the motor, so the reducer above 11KW is required to plan the step-down engine, so as to maintain the reducer and motor from loss.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen