FRP cooling tower is a very common refrigeration equipment in our lives. In order to make it use for a longer time, in addition to basic inspection and cleaning work, we also need to do maintenance work in time.
In general, cooling towers are equipped with water-cooled chillers. For FRP cooling towers that use belt deceleration devices, it is necessary to check the tightness of the belt once every two weeks if it is found during operation. There are inappropriate places that need to be adjusted reasonably. If the cooling tower uses a gear reducer, it needs to be shut down every month to check the oil level in the gearbox. If it is found that the amount of oil inside is not enough, we need to add it in time.
Another thing we need to pay attention to is that the cooling tower needs to be checked for the color and viscosity of the oil every six months of operation. If it does not meet the requirements, it needs to be replaced. In addition, the motor of the cooling tower fan works in a hot and humid environment for a long time. In order to ensure the insulation performance of the cooling tower without the problem of motor burning, it is necessary to test the insulation of the motor once a year.
If we want to ensure that the glass fiber reinforced plastic cooling tower can operate normally, we need to carefully check whether the packing is damaged, and if it is found, it should be repaired or replaced in time. For example, the grease of all bearings on the fan system is generally replaced once a year. Whenever chemical agents are used for water treatment, attention should be paid to the corrosion problem on the fan blades; in order to slow down the corrosion problem, it is necessary to promptly remove the corrosion on the blades. Corrosive substances, and then evenly coated with anti-rust paint.
The preparation of the cooling tower before the formal use and the maintenance during operation. These steps are to allow the cooling tower to perform its functions, so as to extend the service life of the cooling tower, so good inspection and maintenance are definitely necessary for us made. We can observe the glass fiber reinforced plastic cooling tower once a day, so as to ensure its normal operation.
In addition, the glass fiber reinforced plastic cooling tower also needs to be inspected and cleaned during the work, and that part of the work also needs to be inspected in detail to ensure that there are no other problems and we will continue to work. After entering the tower through the inspection door, if we find debris or silt on the bottom basin of the cooling tower, we must also check whether the pipes are blocked, and then use high-pressure water to wash the heat dissipation film and the soil on the bottom basin. , And then drain all the sewage through the drain.
In short, before the FRP cooling tower is officially put into operation, we still need to make corresponding preparations.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen