Today is Thursday, and all of us are going to read the article on cooling tower balancing tubes today.What are the installation matters of FRP cooling tower and balance pipe of cooling tower
Precautions for installation of FRP cooling towers
1. The installation location of the cooling tower should be well ventilated to avoid short circuit of the airflow and the influence of high temperature, high humidity and exhaust of the building or non-clean gas.
2. The number of cooling towers should be designed according to the number of refrigerators. Multiple composite towers shall be set to ensure that the treatment water quantity of a single composite body matches the cooling water quantity of the refrigerator. The cooling tower is not for equipment use.
3. When multiple cooling towers are used in parallel, a balance pipe should be set under the water collecting plate, or an electric two-way valve should be set on the inlet and outlet water pipes.
4. When multiple cooling towers are combined together and the same water collecting plate is used, the air chamber between the parallel towers should be cut off.
Precautions for piping of FRP cooling tower
1, circulating water inlet and outlet pipe control pipe, the best downward, avoid the figure of high control pipe, and can not be higher than the bottom of the tank control pipe.
2, the size of the cooling tower pipe should be installed according to the size of the pipe at the bottom of the tower. Otherwise, too little will affect the effect and too much will waste the material.
3. The circulating water pump should be installed low in normal operation, below the water level of the lower water tank.
4. When two or more cooling towers are used together, and only one water pump is used, the water tank shall be equipped with a balance pipe of the cooling tower to make the water level of the two cooling towers be the same.
Vibration proof hoses (high pressure rubber hoses, etc.) should be used at the inlet and outlet of circulating water above 5 or 4 "(10 cm) to prevent the vibration of the tower body caused by the vibration of the pipeline, and to avoid the damage caused by the rupture of the flume due to improper piping.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen