Cooling tower refers to a type of equipment that can cool water. The water exchanges heat and mass with the gas flowing through it, which reduces the temperature of the water. Why choose the cooling tower chassis for water leakage and its solutions? The cooling tower chassis is the location for receiving water. Because of the water being collected for many months, the chassis leaks in many cases. The following editor will tell you about the key reasons for the leakage of the cooling tower chassis:
1. After a long period of washing, the glass fiber cloth seal is damaged at the connection between the plate and the plate of the water tray. The reason is that most of the cooling towers are cleaned with too many drugs, or the cleaning water tower is at the bottom of the tower. Step on it, causing the chassis to crack.
2. The concrete foundation moves down, and the bearing capacity of the water-passing chassis is uneven. These two situations cause water leakage along the joints of the plates of the water-passing chassis. Cooling towers often overflow, causing too much water in the water pan. Too much load structure can also cause the chassis to rupture.
3. Part of the chassis water leakage is due to the formation of trachoma in the production process of FRP. After a period of selection, trachoma becomes a key channel for water leakage.
The water leakage repair method of the cooling tower chassis. Because the cooling tower circulating water chassis has internal and external seams, and the number is large, the inner side of the pool wall is made of polyester, one cloth and two coating methods:
Drain the water in the pool first, use a blowtorch, air pump, etc. to dry the pool wall, and use an angle grinder to smooth it. While ensuring that the bottom layer is dry and free from floating dust, brush the polyester paint once from the pool wall to the bottom surface of the pool. Roll a 500-wide fiber cloth and roll it toward the outside of the pool wall to 100 heights below the top of the pool wall; after one brushing, one day apart, the non-woven fabric is used to cover the coating once, and then the coating is brushed twice. The procedure is the same. The pool wall and the inner wall of the outlet valve well are made of polyester paint.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen