In the current economic distress, closed cooling towers have sprung up like bamboo shoots after a rain, and the demand-side options have become particularly extensive, but they are also confused in choosing closed cooling towers. On the surface, they feel similar. Can meet the requirements of working conditions. However, during use, a series of problems may be encountered, such as high temperature of the outlet water, high failure rate, motor damage, weathering of fillers, serious panel corrosion, excessive noise, cumbersome maintenance process, etc. How to choose a good closed cooling tower is particularly important Important, trlon editor next analyzes how to avoid problems based on the above situation! Cross flow closed cooling tower
If there is a problem of poor cooling effect in a new set of cross-flow enclosed type, the main reasons can be analyzed from the following aspects:
1. The selection of closed cooling towers is not professional enough, and cannot be combined with equipment operating conditions, regional climate and other factors, to heat the common closed cooling towers such as air compressors, central air conditioners, electric furnaces, test equipment, injection molding machines, continuous casting machines, etc. The operating conditions of the equipment are not understood, and the temperature of the inlet and outlet water is only selected and calculated based on the data provided by the purchaser. The difference in the data is very ridiculous. Professional selection needs to be carried out according to the heat generation process of the equipment, supplemented by the effectiveness of the actual use process of the closed cooling tower, and the statistical effectiveness data is combined with environmental factors such as regional dry bulb, wet bulb, extreme temperature, atmospheric pressure, and altitude. And a series of data on the fouling coefficient of the cooling tower during use, and then perform thermal calculations and redundant selections, so that the cooling effect can be achieved.
2. Insufficient cooling capacity of cross-flow closed cooling tower manufacturers, or insufficient heat dissipation area, economic distress, leading to increasingly fierce market competition, price wars are happening all the time, but after the bloodshed, some manufacturers chose to take the risk. Carrying out the inconsistency of the shortfall of gold, holding a fluke, reduce the cooling tower heat dissipation area, lower the production standard, and bring hidden dangers to the users. After the problems, the normal production work of the users will be affected, and serious problems will be caused to the enterprise. Loss is ultimately harmful to others and self!
Other reasons that affect the insufficient heat dissipation effect of the cross-flow closed cooling tower include: insufficient fan air volume, insufficient heat dissipation filler height, insufficient spray water volume, and insufficient circulating water pump flow. These are the results of insufficient experience in the design process. Such problems are only It is an analysis of a new set of cross-flow closed cooling tower when it was put into operation. After it has been put into use, the above problems need to be analyzed separately. You can find problem analysis methods and solutions in other consultations of the editor. Trlon pays attention to the data collection of each cross-flow closed cooling tower after it is put into operation. The large database combines years of professional experience and zero accident records to provide you with a safe water cooling system solution. We will continue to analyze for you in the later period. Other cross-flow closed What should be paid attention to when choosing cooling tower!
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen