Because of the piping between the cooling tower and the key equipment, when the key equipment first started up and running, the circulating cooling water could not flow to the cooling tower early. How to solve this problem?
Add a water pump, but if the pump lift is enough, the circulating water of the cooling tower cannot be injected into the cooling tower as soon as possible, then the cooling water has leaked under the shutdown condition. If there is no loophole in the pipeline and the water is still insufficient, make up the circulating water of the cooling tower before starting the machine. When you see enough water in the pipeline, start the machine, so as to ensure that the cooling water enters the cooling tower and the main engine early Prevent the water pump from burning down.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen