External turbine: Installed at the position of the motor outside the wind tube, and is driven by a soft connection to the gearbox to drive the fan to rotate.
Comparison of 5 aspects of similar cooling tower products:
1) The external water turbine is installed on the motor position outside the cooling tower air cylinder, and the water inlet and outlet pipe connections of the water turbine are all connected outside the air cylinder.
2) The external water turbine is installed outside the cooling tower fan. As long as the inlet and outlet valves of the turbine are closed and the bypass valve is opened, the system can start normal spraying (without affecting the production process), and can be maintained and repaired at any time. There is no need for hoisting to enter the site, saving time and money.
3) The external water turbine is installed at the click position outside the cooling tower fan, and the drive shaft is connected to the designed special gearbox.
4) The working condition of the external turbine is outside the wind tunnel, away from the high-heat and humid environment, and various sensing devices can accurately transmit information.
5) When the flow is much lower than the design value, the external turbine can also be combined and split to work, so that part of the flow of the cooling tower next to it can be used to meet the turbine's work, and then distributed to the cooling tower next to the average spray . Merging and re-dividing not only solves the energy-saving transformation effect of low-flow cooling towers, but also effectively reduces the start-up time of the side tower motors of low-flow cooling towers (usually only for 7, 8, and 9 months), thereby realizing the improvement of an external type The water turbine can save electricity for one and a half motors.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen