The main reasons for regular maintenance and replacement of cooling tower packing:
1. When the cooling tower packing has been used for a long time, there will be an old condition, and some of the packing will be separated, resulting in the decline of the heat transfer effect of the cooling tower. Affect the operating efficiency of the refrigeration unit and consume a large amount of calories. Fragmented cooling tower filler is easy to enter the condenser air-conditioning copper pipe of the unit along with the operation of the refrigeration pump, causing the air-conditioning copper pipe of the condenser of the unit to have a time delay and need to be replaced immediately;
2. The application of cooling tower fillers is poor in natural environment, and the gaps between the fillers are blocked, which affects the heat transfer effect. If the water body of the water tower is usually cleaned in 1 month, daily maintenance is also required, most of which can be used until the end of its service life. . There will be a lot of sediment and bacteria in the filler for two years when the water body is not good, and the heat rejection capacity is poor, and the air conditioning and refrigeration effect will not work. At this time, the filler can only be replaced;
3. Do not use strong alkali during cleaning and maintenance of the cooling tower. If the application will corrode the packing, the packing will not be damaged and need to be disassembled. The temperature of the packing is between 50°C and 68°C. If the cooling water system is not well done Maintenance work, and the deformation of the filler sheet due to the high water temperature will shorten the service life of the filler. In serious cases, the cooling tower filler must be disassembled to ensure the heat transfer effect.
The key points that must be paid attention to when dismantling and replacing cooling tower packing are as follows:
(1) The wave pattern between the single side and the single side must be obliquely overlapping, so that it has excellent heating friction resistance;
(2) The rectangular packing assembly module is most suitable for the square tower. There will be gaps in the circumference of the circular cooling tower. It is necessary to fill with a different total number of single-sided packing according to the size of the gap;
(3) The cooling tower packing should be cleaned regularly at ordinary times. If you do not pay attention, if the blockage of the packing is serious, it must be dismantled and replaced as a whole, which will increase the cost.
Guangdong Kangming Energy-saving Air Conditioner focuses on the product research and development, design, production, sales, installation, cooling tower maintenance and refrigeration engineering of central air conditioning cooling equipment. Cooling tower maintenance and transformation related businesses include: undertaking the dismantling and replacement of cooling tower fillers of major brands, dismantling old cooling towers and replacing them with new ones, dismantling and replacing cooling tower accessories, cooling tower noise reduction, cooling tower anti-corrosion and leakage repair, cooling tower equipment overhaul, Circulating water cooling project, etc. The scope of service covers Dongguan, Shenzhen, Guangzhou, Huizhou, Foshan, Zhuhai, Zhongshan, Shantou and other places, focusing on becoming a supplier of high-quality cooling systems and supporting related businesses.
Guangdong Trlon Energy-saving Air Conditioning Equipment Co., Ltd.
Company Address： 1916A, Block A, David Donglong Business Building, Longhua, Longhua District, Shenzhen